Why our Runtime Gate Sampling Status always show "KO" and we cannot communicating with IO devices?We use Runtime/X for this application. We import project from another running Winlog SCADA.
General discussion about Winlog.
2 posts • Page 1 of 1
Who is online
Users browsing this forum: No registered users and 2 guests